XFP 16 Zone Repeater Panel (all protocols)
- Brand C-TEC
- Model XFP510-16
Ex Tax: 10.00 лв.
Can be used to repeat the functions of an XFP Main panel at remote parts of a site (e.g. all potential fire service entrances).
Offers all of the functions and controls of an XFP Main panel (access levels 1, 2 and 3).
Includes an on-board fault relay.
Requires its own dedicated Mains power and battery back-up supply.
A maximum of eight XFP Repeaters can be connected to one non-networked XFP Main panel.
Communication between the XFP Main panel and Repeater requires a CFP761 network driver card (fitted as standard in all XFP510-16s, available as an optional extra on Main XFP 16 Zone panels).
Repeater network wired in 1.5 mm2 two-core screened fire resistant cable. Network length must not exceed 500 metres
|Technical data fire alarm control panels|
|Power supply:||230V 50/60Hz.|
|Internal power supply:||27Vdc|
|Total output current limited to:||1.4A @ 230Vac (Imax.A 210mA; Imin. 40mA).|
|Max battery size and type:||2x 3.2Ah/12V|
|Quiescent current:||<50mA (loop unloaded).|
|Auxiliary relays:||Fault (Failsafe; Capable of switching 1A @ 30V DC; Must not be used for switching Mains voltages).|
|Display:||2 line x 40 character backlit display|
|Indicators:||16 Zonal LEDs, General Fire; Energised; Pre-Alarm; Remote Output Activated; Remote Output Disabled; Accessed; Disablement; Test; Silenced; General Fault; System Fault.|
|Construction & finish:||Plastic lid and base; RAL7035 textured.|
|Dimensions:||380 W x 235 H x D 96 mm;|
|Weigh:||1.8kg (without batteries).|
|Operating temperature:||-5ºC to +40ºC|
|Approvals/certifications||Certified to EN54-2/4 by the LPCB (0832-CPD-0772).|